Pipes Repair-How To Repair Pipe Weld Joints
Pipe weld joints are one of the weakest links within the piping system. Pipe leaks often occur around the weld joints due to various reasons. Some of the reasons include:
- Lack of fusion
- Corrosion at heat affected zone
- Crack (due to heat stress, solidification, hydrogen-induced)
- Inclusion of slag
In order to arrest pipe leaks without applying hot works, it shall be carried out using the cold repair methods of epoxy repair compounds and pipe repair kits.
Pipeline Data & Information
In order to perform an effective pipe repair and rehabilitation work, it is mandatory to understand the pipeline operating conditions. Pipeline data including operating pressure, temperature, pipe size and pipe medium should be gathered. All effective pipes repair and rehabilitation techniques should follow international standards and guidelines in accordance to ASME PCC2 and ISO 24817 standards and requirements.
Detailed Engineering Calculation and Application Method of Statement
Based on the pipeline data gathered, the manufacturer would design and provide a detailed engineering calculation and application technique for the pipes repair and rehabilitation works. It is also necessary to ensure that the applicator is well-trained to apply the pipe repair wrapping products as well as a site risk assessment has been performed prior to work commencement. Proper Personnel Protective Equipment should be worn and risk mitigating/ reducing steps employed to minimize or avoid all unnecessary risks.
Surface Preparation of Affected Pipe Section
In general, pipe surface should be prepared to SA2.5 standards whenever possible. In order to ensure good bonding between the epoxy repair compounds with pipe surface, it is necessary to ensure that the surface profile has met minimum of 60 microns roughness. Thereafter, repairing of pipes should begin as soon as pipe surface works has been completed.
Rebuilding of Affected Pipe Section
The first step in all rehabilitation works is to ensure that all pipe surfaces have been rebuilt to even surface profile. The epoxy resin or repair putty should be well-mixed in accordance to manufacturer instructions and applied onto the affected surfaces while ensuring there are no air entrapments. The applied coating thickness and length would be in accordance to the engineering calculation provided that is specific to the repair requirements.
Pipe Repair Wrapping
The final step is to apply the pipe repair tape. Wrap the repair tape (e.g. fiberglass repair tape) approximately 200mm before start of defective location. Wrap the pipe as tightly and evenly as possible, pulling with sufficient strength during each layer of wrapping. Apply the entire roll over the pipe surface with at least 50% overlap for the entire pipe repair sectionin accordance to Engineering Calculation Report. Repeat the wrapping for a specific number of layers of the repair tape and finally tapering off with approximately 25mm over each wrapping layer. The wrapping direction can be alternated between subsequent layer of wrapping so as to increase its mechanical strength in various directions.
Inspection of Pipeline Repair & Rehabilitation
Inspect the repaired pipeline for any visual defects. Check that the repair thickness and length complies with the requirements stated in the Engineering Calculation. Allow the repaired area to be cured for several hours and the repairing of pipes is completed.